## Correct Cooling Of An Industrial Cabinet

To determine the correct model for your application, it is first necessary to determine the total heat load to which the control panel is subjected. This total heat load is the combination of two factors — heat dissipated within the enclosure and heat transfer from outside into the enclosure.

## To Calculate Btu/hr.:

1. First, determine the approximate watts of heat generated within the enclosure. Watts x 3.41 = Btu/hr.

2. Then, calculate outside heat transfer as follows:

a. Determine the area in square feet exposed to the air, ignoring the top of the cabinet.

b. Determine the temperature differential between maximum surrounding temperature and desired internal temperature. Then, using the Temperature Conversion Table (below), determine the Btu/hr./ft.2 for that differential. Multiplying the cabinet surface area times Btu/hr./ft.2 provides external heat transfer in Btu/hr.

## Help & Tips

• #### What is PIDWhat is PID+

A proportional–integral–derivative controller (PID controller) is a generic control loop feedback mechanism (controller) widely used in industrial Read More
• #### Differences Between Star & Delta ConnectionsStar & Delta Connections+

In the world of circuitry the star (or "Y") and delta connections are two basic ways to Read More
• #### Correct cooling of an Industrial CabinetIndustrial Cabinets+

To determine the correct model for your application, it is first necessary to determine the total heat Read More
• #### Optical Character Recognition (OCR) +

Optical Character Recognition, commonly known as OCR, is simultaneously machine-readable and human-readable text. Common industries and applications
• #### Optical Character Verification (OCV) +

Optical Character Verification, or OCV, is a machine vision software tool used to inspect the print or
• 1
• 2